Generac Power System's commercial line of standby generators feature exclusive Quiet-Test for ultra-quiet operation during the unit's weekly self-testing period. When normal utility power is present, Quiet-Test allows the generator to run at reduced speeds, thereby lowering sound pressure by as much as 12dB. This is especially important in areas where residences or other businesses are close by. Clean, natural gas fueled. No diesel fuel storage or exhaust emissions to worry about. Great for larger homes and businesses. HTS transfer switches sold separately. U.S.A All sales final. All warranty work will be performed in the field, by the manufacturer. Engine Generac 6.8L V-10, Battery Included No, Rated Watts LP kW 150, Phase 1, Noise Level dB 76, Battery Required Yes, Transfer Switch No, Mounting Pad No, Start Type Automatic, Engine Speed RPM 3,600, Dimensions L x W x H in. 115 3/16 x 36 25/32 x 54 25/32, Auto Shutdown Yes, Enclosure Yes/ Steel, Volts 120/240, Fuel Type Liquid propane, UL Listed Yes, Engine Cooling Liquid. Auto Shutdown Yes Low oil pressure, high temperature, over speed and/or overcrank Meets 2009 EPA standards All generator sales are final Standby generators require installation involving permanent outdoor placement, electrical wiring and fuel source connections. We recommend the use of a trained professional for final connections of gas and electric.
Average Customer Rating:
(1 Review) 1
Rating Summary(1 review)
1 of 1(100%)would recommend this product to a friend.
Customer Reviews for FREE SHIPPING - Generac Commercial Series Liquid-Cooled Standby Generator - 150 kW, 120/240 Volts, LP, Model# QT15068AVAC
Review 1 for FREE SHIPPING - Generac Commercial Series Liquid-Cooled Standby Generator - 150 kW, 120/240 Volts, LP, Model# QT15068AVAC
150 KW Generator LP
March 14, 2011
"The units shipping packaging was poor at best. The manufacture should realize that the units being shipped will be handled by numerous facilities once it leaves their manufacuturing facility. The unit arrived with bent access doors (they were fixed but still shows signs of the dents/they are operational), i had to accept the unit due to timing of deployment. The bottom rail flang that sits on the concrete foundation and is used for permanent attachement to the concrete foundation is to small to accomodate a proper sized anchor. There should be consideration to theft of the unit, the permanent attachment should be inside the unit. The lock to the access doors should have a higher quality mechanism and consideration should be placed on theft. The installation guideline manual and drawing OF6289 dimensions for the location of the stud out for electrical entry are poor and are shown on the top and side views of the gen-set, no foundation plans at all, there should be a plan view of the foundation.
The unit overall is what was expected and I will be purchasing additional units of a smaller size this year."
Describe Yourself: Professional
3out of3found this review helpful.
Share this Review:
Thank you! You have successfully submitted a comment for this review.